220 Volt Systems - General Information
220 Volt, 50 amp, 4 wire - GFCI Breaker Required 2 Hots, #6 AWG1 Neutral, #6 AWG1 Ground, #6 AWG#8 Bonding Required
Straight 220V hook-up requires a dedicated line of 50 AMPS (consult your electrician). This wiring will be hard wired directly to your pack by your electrician. No plug is needed. 50 AMP breaker must be GFCI protected.
110 Volt Systems - General Information
110 Volt, 20 AMP, 3 wire1 Hot, #12 AWG1 Neutral, #12 AWG1 Ground, #12 AWG#8 Bonding Required
Straight 110V hook-up requires a dedicated (1 hot, 1 neutral, and 1 ground) receptacle (consult your electrician); a 20 AMP breaker is required. Spa & Tub Manufacturer's provides a cord from the equipment pack with a three-prong plug. Use of extension cords is a violation of City and State Regulations.
IMPORTANT: Spa & Tub Manufacturer's, Inc. is not required to do any electrical hook-ups. A licensed electrician must do all electrical work.
NOTE: Always check local and state codes for wiring requirements that may exceed N.E.C. Copper Wire Only